*E.F* Lightning Carrier
WEIGHT: 1.5 kg / m
DIAMETER: 31 mm
INSTALLATION: Metallic masts, mounting rings, and guyings must not be used.
The lightning Carrier shall consist of two copper conductors, insulated from one another and from the structure. The arrangement of the conductors shall be such that one is coaxially placed about the other. Each conductor shall have a minimum of 35 mm cross sectional area of electrical grade cooper.The insulating medium between inner and outer conductor shall be able to withstand a 1 / 50 microosecond impulse not less than 250 Kv
The inner conductor shall be capable of direct crimp press to the base of the air terminal
The downconductor shall be installed in accordance with manufacturer’s instructions and shall not be subject to bends of less than 0.6 m in radius.
Lightning stroke on the E.F. Carrier System safely conveyed to earthing through the E.F. Lightning Carrier – without electrification of the structure.
CV. Mitra Technik Global
JL. Raya Tropodo No.57 Waru-Sidoarjo.
85879862931 ( Mudrik )
Cab.purwokerto ; 085292554416